category：Machinery and industry equipment / date：2022-05-12 00:36:50 / browse：71 / comment：3
On load commissioning:Power transformerPort Limon,The proper selection of Anhui dry-type transformer has a key effect on improving the safety and smooth operation of power system software. In the above original text, we have already mastered the structure and characteristics of dry-type transformer. In this part, we will describe how to select dry-type transformer according to the load characteristics and application environment of dry-type transformer.Turn off the gate valve (butterfly valve) of the left and right tablet computers of the heat pipe radiator to isolate the oil in the heat pipe radiator from the oil in the tank,Port LimonOil immersed box transformer, so as to reduce the working pressure and leakage. After the leakage location is determined, appropriate surface treatment shall be carried out, and then Fushi blue raw materials shall be selected for sealing treatment.Kapiri Mposhi,What is the important role of power transformerOil leakage at electric welding positionThe noise of dry-type transformer belongs to low-frequency noise. In a small area, most of it is scattered according to the building structure. This kind of low-frequency noise is scattered to the household house according to the house building, and then causes gas vibration noise, the dispersion spacing and adverse effects are very large.
In terms of the place of use, dry-type transformers are mostly used in & ldquo; Fireproof and explosion-proof type & rdquo; It is easy to use in large and medium-sized engineering buildings and multi-storey buildings; The oil immersed transformer because of & ldquo; Accident & rdquo; There is likely to be oil or leakage after fire, and most application places leading to fire accidents are easy to choose in large and medium-sized engineering buildings and multi-storey buildings;In fact, apart from the application of the Finance Bureau the industry has been trying to formulate and upgrade transformer commodities according to the specifications, so as to promote the improvement of energy consumption level of transformer commodities.The input and output three-phase power lines shall be connected to phase a, green and red bus duct of transformer terminal board. The zero line shall be connected to the neutral zero line of transformer voltage, and the grounding wire, transformer casing and its transformer point shall be connected to each other. At ordinary times, the ground wire and zero wire are led out by the neutral wire of the transformer. (for example,Port LimonHow much is 500KVA box transformer, the transformer box shall be matched with the ground wire mark of the shell and connected with each other). Check the input and output lines to ensure they are appropriate and accurate.Customer first,Port Limon10kV distribution transformer,The manufacturing process of dry-type transformer is very process, and must be technically as a certain pillar. Only in that way, the performance of dry-type transformer will be more stable. What are the common manufacturing processes and steps of dry-type transformer?The bearing capacity of each load is different. Generally, dry-type transformer should operate under rated capacity, while oil transformer has better load working capacity.When oil samples are used, the safety and fire safety technical specifications on the spot shall be strictly implemented.
Some are tied with plastic tape, because the socket can not be pressed firmly during installation, and there is still oil leakage without sealing effect.Safety and health,When the full load test is carried out and everything is normal, the load can be connected.The equipment can eliminate the shortcomings found in the patrol inspection clean the porcelain waterproof casing casing, remove and replace the cracked or brittle leather pad, check and tighten the node, replenish the oil with less oil, check and replace the silica gel of the breathing mask, etc.If you want to check the activated carbon fiber for the hanging cover, first take out the low-voltage waterproof sleeve and the on load transformer power switch, then lower the bell cover anchor bolt of the large cover, slowly hang the galvanized steel wire rope with sufficient lifting net weight on the commonly used earrings wear round steel from top to bottom in the surrounding screw holes, and count the spacing and specifications for easy reinstallation. At the same time, the cable wind shall be added on all sides to ensure that the core international body will not be damaged during the whole lifting process. After lifting for mm, stop the lifting, stabilize the bell cover, and check the bearing capacity of the lifting core, center of gravity and Jack. After everything is normal, lift it again until the bell cover exceeds the relative height of the body, and rotate the crane to place the bell cover on the clean skid.Port Limon,Use fiber materials to seal the bolts to achieve the goal of controlling leakage. The other is to screw out the bolt (nut), wipe the Fushi blue film remover on the surface, and then tighten it after wiping the raw materials on the surface. After drying, the treatment goal can be achieved.Noise solution of dry-type transformerOil leakage of heat pipe radiator